Recent Review: These are the best guys in the business, hands down. Israel, Ben and Dan were absolutely amazing. We had bought a new house, and we had issues where the south end of the house was not getting very much air flow. We had several other HVAC folks evaluate it, one even attempted to repair it, but ultimately none came up with a good solution. Israel told me that it was due to a 90 degree jump the ductwork had to do to get to the south end of the house, and he explained in detail why that is a bad thing, and why the air is having such trouble making it over that bend. They removed the whole duct work going to the south end, and re-positioned it to flow in a straight line, having to build a custom duct piece that moved a few degrees to the left to avoid our stairs, then back again. Dan did an amazing job installing this duct and getting everything to fit just perfectly. After they were done, air flow through our 4200 SQ foot house was strong and equal through all the vents. Next: we had a problem where the AC unit was not cooling down the house. We had several HVAC professionals come in and evaluate the situation. Israel was the only one that walked in, took a look aroung the house, asked me what the square footage of the house was, took one look at the AC unit, and told us that there was no way that unit could cool down a house of that size. He suggested at least a 4 ton unit, but we went with a 5 ton unit just to make sure, and we got an American Standard AC unit, which is what we wanted in the first place. We also had a problem with strong winds knocking out our heat in the winter. Israel came up with a solution, moved the intake/outake pipe from the north side of our house to the east side, and we have not had any issues with our heat since then. We also asked him to re-locate the AC unit from the north side to the east side as well, to get it out of the wind, which he also did while putting in the new AC unit. There was a hole left in our stucco from where the old AC unit had been. They sealed the hole professionally, it looked fantastic when they were done. They even went so far as to try and match the paint, and repaint over the patch area. After all their hard work, our HVAC system is absolutely fantastic, and works like a champ! I cannot recommend these amazing folks enough, and I will be using them from now on for any and all HVAC work.